UVC is light photons produced between 100 to 280 nanometers (nm) wavelengths.
The best germicidal wavelength is 280 nm.
NEXNORD’s Titan fixtures are field-serviceable so the parts can be easily replaced on site and at the end of fixture life without having to replace the entire fixture. All Titan parts are recyclable and reusable, sothey do not end up in landfill. In addition, the replaced parts are returned to NEXNORD to be retrofitted and reused – it is ‘Cradle to Cradle’ design. NEXNORD also applies RoHS(restriction of hazardous substances) in the Titan design therefore, it does not contain any mercury, lead or other hazardous materials. The Titan fixture is 100% recyclable.
120-277v,347v & 480v.
5 years limited warranty.
Yes, UVC light is harmful.
- You must wear UVC protective eyeglasses such as these:
NEXNORD will pride these glasses to the installers and service personnel at no cost for your protection.
- You must wear long sleeves shirt, pants and latex or work gloves so no part of your skin is exposed directly to the UVC light.
- Do not look directly at the UVC light.
- Do not expose skin under the UVC light.
No UVC light is not visible. NEXNORD adds a faint blue glow on the LEDs to show that they are on.
Is there a difference between UVC light generated by the old mercury lamp technology and the state-of-the-art Titan UVC LEDs?
No, there is no difference between the UVC generated using the old fragile mercury lamps or the sun.
Ozone is created between 100-240nm wavelength. The Titan UVC LEDs are 280nm. Titan’s 280nm wavelength has 127% more ‘virucidal’ eradication power than the traditional mercury lamp at 256nm as per Tokushima University Study conducted by the Biomedical Graduate Department.
Mercury Lamps last 9,000 hours and needs to be continuously powered on, requiring annual replacement.The Titan UVC LED rated life is 25,000hrs and only needs to be on when there is airflow in the duct. Therefore, at 30% usage,it will last for over 9 years before the LED circuit board needs to be replaced (only the circuit board needs to be replaced and not the whole fixture.
|ITEM||TITAN UVC LED SYSTEM||MERCURY TWO (2) LAMP SYSTEM|
|Initial Cost||$3,000 x 2 = $6,000||$4,600|
|Tube Replacement Cost (Over 9 Years)||$0||$130 x 2 lamps x 9 = $2,340|
|Labour Maintenance Cost (Over 9 Years)||$0||$125/hr x 2hrs x 9= $2,250|
|Energy Consumption ($0.15/kwhr Delivered||$61.32||$315.36|
The number of units required per installation is determined by the Length and Width of each air return duct dimension to each Air Handling Unit/Roof Top Air Handling Unit (AHU/RTU) and the Cubic Feet per Minute (CFM) air flow rate in these air return ducts.